OXY TECH 6000 is an aqueous solution of sodium bisulfite used as an oxygen scavenger for the control of oxygen corrosion in pre-boiler systems. For a complete boiler water treatment program, Oxy Tech 6000 should be combined with other products for control of deposition in the boiler and for control of corrosion in the return line system.
4x1 gallon, 5 gallon, 15 gallon, 55 gallon, 330 gallon, Bulk
Features and Benefits
Oxy Tech 6000 should be fed to the storage section of the deaerator or to a point as far upstream from the boiler as possible. The correct dosage will vary depending on the dissolved oxygen content of the feed water and the sulfite residual desired in the boiler water. Under most circumstances, a sulfite residual (as SO3) of 20-40 ppm in the boiler is recommended. Consult your Spray Chem Representative for detailed usage instructions.
DANGER: AVOID CONTACT WITH SKIN OR EYES. DO NOT TAKE INTERNALLY. AVOID BREATHING VAPORS.
Eyes: Flush immediately with copious amounts of tap water or normal saline for a minimum of 15 minutes. Take exposed individual to a health care professional, preferably an ophthalmologist, for further evaluation.
External: Wash exposed area with plenty of soap and water. Repeat washing. Remove contaminated clothing and wash thoroughly before reuse. If irritation persists, consult a health care professional.
Ingestion: Do not induce vomiting. Drink solution of vinegar and water followed by clear water. Get immediate medical attention.
DOT Classification Shipping Name
Non regulated material
Manufactured in accordance with regulations established for food plants operating under USDA guidelines.